An alternate system uses a fog or good mist injected in to the intake air stream. Although many commercial systems are available, growers can assemble and set up their own system using a high pressure piston pump and fog nozzles. The essential components are proven in Fig. 1. A two-stage system managed by a two- stage thermostat allows more water to be applied on excessively warm, bright days. Temperature settings should be 5-10°F apart.
Algae development in the pads can become a problem which will reduce the effectiveness of the machine and result in accelerated deterioration of the pads. The addition of an algaecide to the drinking water supply can help in control.
It is desirable, especially in hard water areas, to add a wetting agent to the water to obtain more uniform wetting of the pads. A commercial material or liquid home detergent at the price of 2 tablespoons per 100 gallons may be used.
Drinking water for the pads ought to be clean and lower in mineral content to prevent clogging and coating of the pads. A pump, pipes and gutters are accustomed to recirculate the drinking water. A flow rate 113 gallon each and every minute per linear foot of pad system ought to be provided to make certain adequate wetting.
In the most typical coolant system (fan and pad), the fans draw air through wet pads that extend the length of one endwall or sidewall. Aspen and covered cellulose are normal pad materials that always have life of 1 to 3 years. Approximately one sq . foot of pad are is needed for 20 square ft of floor area.
Have you attempted Greenhouse Exhaust Fan? Make sure to visit our website and also find out a lot more.